Short Transmission Line:
For Short Transmission Line of length 100 km or less, the total 50 Hz shunt admittance* (jωCl) is small enough to be negligible resulting in the simple equivalent circuit of Fig. 5.1.
This being a simple series circuit, the relationship between sending-end receiving-end voltages and currents can be immediately written as:
The phasor diagram for the short line is shown in Fig. 5.2 for the lagging current case. From this figure we can write
Expanding binomially and retaining first order terms, we get
The above equation is quite accurate for the normal load range.