The assembly of apparatus used to change some characteristic (e.g. voltage, ac. to dc., frequency, p.f. etc.) of electric supply is called a Substation.
Sub-stations are important part of power system. The continuity of supply depends to a considerable extent upon the successful operation of sub-stations. It is, therefore, essential to exercise utmost care while designing and building a sub-station. The following are the important points which must be kept in view while laying out a sub-station :
- It should be located at a proper site. As far as possible, it should be located at the centre of gravity of load.
- It should provide safe and reliable arrangement. For safety, consideration must be given to the maintenance of regulation clearances, facilities for carrying out repairs and maintenance, abnormal occurrences such as possibility of explosion or fire etc. For reliability, consideration must be given for good design and construction, the provision of suitable protective gear
- It should be easily operated and maintained.
- It should involve minimum capital cost.
Classification of Substation:
There are several ways of classifying sub-stations. However, the two most important ways of classifying them are according to
Service requirement and
1. According to service requirement: A sub-station may be called upon to change voltage level or improve power factor or convert a.c. power into d.c. power etc. According to the service requirement, sub-stations may be classified into:
(i) Transformer sub-stations: Those sub-stations which change the voltage level of electric supply are called transformer sub-stations. These sub-stations receive power at some voltage and deliver it at some other voltage. Obviously, transformer will be the main component in such sub Most of the sub-stations in the power system are of this type.
(ii) Switching sub-stations: These sub-stations do not change the voltage level i.e. incoming and outgoing lines have the same voltage. However; they simply perform the switching operations of power lines.
(iii) Power factor correction sub-stations: Those sub-stations which improve the power factor of the system are called power factor correction sub-stations. Such sub-stations are generally located at the receiving end of transmission lines. These sub-stations generally use synchronous condensers as the power factor improvement equipment.
(iv) Frequency changer sub-stations: Those sub-stations which change the supply frequency are known as frequency changer sub-stations. Such a frequency change may be required for industrial utilisation.
(v) Converting sub-stations: Those sub-stations which change a.c. power into d.c. power are called converting sub-stations. These sub-stations receive ac. power and convert it into d.c. power with suitable apparatus (e.g. ignitron) to supply for such purposes as traction, electroplating, electric welding etc.
(vi) Industrial sub-stations: Those sub-stations which supply power to individual industrial concerns are known as industrial sub-stations.
2. According to constructional features: A sub-station has many components (e.g. circuit breakers, switches, fuses, instruments etc.) which must be housed properly to ensure continuous and reliable service According to constructional features, the sub-stations are classified as :
1. Indoor sub-stations: For voltages upto 11 kV, the equipment of the sub-station is installed indoor because of economic considerations. However, when the atmosphere is contaminated with impurities, these sub-stations can be erected for voltages upto 66 kV.
2. Outdoor sub-stations: For voltages beyond 66 kV, equipment is invariably installed out It is because for such voltages, the clearances between conductors and the space required for switches, circuit breakers and other equipment becomes so great that it is not economical to install the equipment indoor.
3. Underground sub-stations: In thickly populated areas, the space available for equipment and building is limited and the cost of land is high. Under such situations, the sub-station is created The reader may find further discussion on underground sub-stations.
4. Pole-mounted sub-stations: This is an outdoor sub-station with equipment installed overhead on H-pole or 4-pole structure. It is the cheapest form of sub-station for voltages not exceeding 11 kV (or 33 kV in some cases). Electric power is almost distributed in localities through such sub For complete discussion on pole-mounted sub-station.
Comparison between Outdoor and Indoor SubStation:
The comparison between outdoor and indoor sub-stations is given below in the tabular form :
From the above comparison, it is clear that each type has its own advantages and disadvantages. However, comparative economics (i.e. annual cost of operation) is the most powerful factor influencing the choice between indoor and outdoor sub-stations. The greater cost of indoor sub-station prohibits its use. But sometimes non-economic factors (e.g. public safety) exert considerable influence in choosing indoor sub-station. In general, most of the sub-stations are of outdoor type and the indoor sub-stations are erected only where outdoor construction is impracticable or prohibited by the local laws.